Kohler 20RESCL-200SELS 20kW Generator with 200A SE Transfer Switch Features:
Natural Gas Fuel Requirements – 20RESCL-200SELS (New) Fuel Supply Pressure kPa (in. H2O) Natural Gas - 0.9-2.7 (3.5-11)
Natural Gas Fuel Requirements – 20RESAL-200SELS Fuel Supply Pressure kPa (in. H2O) Natural Gas – 1.2-2.7 (5-11)
The differences in the design changes made to the 20RESCL-200SELs are an upgrade to the engine mounting block and the gas regulator. They were upgraded to allow for a lower gas pressure (3.5” water column). Benefit of the new 20RESCL-200SELS - if you have an older gas meter with the new 20RESCL – an upgrade may not need to be made to the gas meter-saving you time in permitting and not upgrading you gas meter (cost savings).
If you need reliable back-up power for your whole home, the KOHLER 20RESAL-200SELS 20kW generator is an ideal choice that can provide you with 20,000 watts of electricity to ensure that you and your family stay calm and comfortable even during the worst that Mother Nature has in store. This KOHLER generator is designed to switch on automatically in as little as 10 seconds when your power goes out, allowing you to enjoy real peace of mind even when you are away from home. The load-shedding capability of the KOHLER 20RESCL-200SELS model ensures that the most critical systems in your home receive consistent power even when your demand exceeds the available supply. Because the KOHLER 20RESCL-200SELS 20kW generator can power your entire home, it can minimize the inconvenience of temporary power outages and can keep you and your family safer during major storms. It is controlled and regulated digitally to ensure steady and safe power for your climate control systems, major appliances and delicate computer or entertainment equipment. Voltage regulation is managed within a variance of plus or minus one percent; this ensures the best possible protection for all your household systems and appliances. The LCD display features back lighting to ensure clear visibility. The KOHLER 20RESCL-200SELS can be configured to run on propane or on natural gas. This allows you to enjoy added options when installing your back-up generator. The unit is designed for outdoor installation and runs as quietly as a typical central air conditioning unit, making it an excellent choice for residential use. The rugged enclosure is corrosion resistant to protect against the elements and has been impact tested under ultra-cold conditions of 30 Fahrenheit degrees below zero. By installing the KOHLER 20RESCL-200SELSSA7 generator to provide reliable back-up during power outages, you may even be able to increase the value of your home at the time of resale. Reliable back-up generators are a hot selling point in the modern real estate marketplace and offer real security for you and your family even in the worst weather. The KOHLER line of generators is among the most respected in the industry. These elite units have won numerous industry awards for excellence; in fact, a Kohler generator was named the Most Valuable Product for 2010 by Building Products magazine. You can buy with confidence because the KOHLER 20RESCL-200SELS generator system is backed by the KOHLER five-year, 2000-hour protection plan that protects you against unexpected failures. Fully loaded with electronic speed control and air-cooled for optimal performance, the KOHLER 20RESAL-200SELS 20kW Generator with 200A SE Transfer Switch delivers the reliable electrical power you need to keep your family safe and secure even in the worst weather conditions.
Kohler 20RESCL-200SELS 20kW Generator features:
- PowerBoost™ technology provides power to start large loads such as central air conditioners without dropping power to other appliances
- Extraordinary peak motor-starting capacity: 20RESCL at 41kVA at 240V
- Premium power quality delivers exceptional digital voltage and frequency regulation along with low levels of harmonic distortion to protect sophisticated electronics
- Powered by reliable KOHLER Command PRO® engine, designed and tested for tough commercial applications; with hydraulic valve lifters to eliminate need for lengthy break-in periods and expensive valve adjustments; operation speed is 3600 rpm (the standard for air-cooled generators)
- Compatible with optional OnCue® Plus and OnCue® Plus Wireless Generator Management Systems, and Programmable Interface Module (PIM)
- Also compatible with Load Control Module (LCM) or Load Shed kit with single-phase generators only
- Comes with either an RXT 100-amp indoor-rated automatic transfer switch with 16-circuit load center or RXT 200-amp outdoor-rated service entrance rated automatic transfer switch with load shed kit
- Quiet, neighborhood-friendly operation with sound levels similar to a typical central air conditioner
- Stylish corrosion-proof enclosure impact tested to -30°F
- Runs on either natural gas or liquid propane (LPG) with simple switching between natural gas and LPG in the field
This kept us very comfortable through hurricane Ida. I have two central ac units and 3 water heaters, hot tub, all electric house. We operated as normal for the entire time we were without power. The lights would flash when the ac would come on, but just for a half a sec. It's hardly the volume of an ac unit. It's loud as can be, but its a great piece of equipment. Easy install.
I purchased this generator in 2014. In the six years I owned that home, the only service calls I had were my annual tune up and oil change (which I actually never called for, the company I purchased it from automatically sent out a tech. Every Tuesday at 1 pm, the generator did its weekly check up cycle (it takes control of the house’s power supply and runs for a few moments). I lived on the North Shore of Long Island, an area often plagued by hurricanes and service outages (a majority of areas are still served by overhead power lines / service interruptions could be a blown transformer or a car vs pole accident). Without any major storm, we could still count on several outages per year. The Koehler generator ran (and is still running, per my neighbors) ran extremely well (I could have run my own power company, the amount of neighbors Orange extension cords snaking from my property during outages!). The original reason I purchased Koehler was the composite cover - with the salt air, competitors covers rust through (thus exposing the generator) very quickly. Now, I am building a new home and I would not even consider anything but a Koehler!
Just finished the final installation of the new Kohler unit on 6/9/2020. It was a sunny day and at 5PM the power went out. Large tree had fallen on power lines. The unit fired up snd everything ran perfect for the next 13 hours. Wow timing could nt have been better.
The AP team was fantastic from start to finish.
Our investment has already paid for itself.
A few months ago I bought this generator, and it went on sale during the 30 day period. So I am requesting that reimbursement. I just did it so not sure they have seen my request yet, but I'm certain they will honor it. I have already given information to my local installer as others are interested in this unit.
We received the generator in a timely manner. The deliverer was tremendous and was abot to get the generator as close to the installation point as possible.
Generator was installed on 10/27. We have only needed to use it once so far. It performed as it was supposed to.
You can't beat Kohler quality and I was very pleased with the looks of the generator. Great assistance on the phone in selecting this generator no high pressure sales tactics. In fact just the opposite, they just wanted to make sure that whatever brand generator I selected was going to suit my needs.
Great Company to order from. Fast shipping and great tracking. They were really patient on the phone with as I called multiple times before purchasing. No hard sales pitch or pressure. Can't say enough about this online retailer. The Kohler generator is performing as it should
Perfect transaction on my purchase of the Kohler 20kW generator with transfer switch. It arrived in 2 days if you can believe that. Much sooner than expected. Installed in February and has run flawlessly and handled a 4 hour power outage without a hitch.